CALSAFE ALERT - IMPORTANT
Office of the State Fire Marshal Fire Extinguisher License renewal requirement change. CALSAFE has received a number of phone calls and emails regarding notices sent to Licensees from the OSFM.
Fire Extinguisher Requirements
Do you know the fire extinguisher requirement for an Asphalt Kettle? If you were at the CALSAFE Annual Meeting you would have leaned the answer to this and many more extinguisher requirements that are not in Title 19 but in the California Fire Code. Read more about the requirements from the Fire Code you may not be aware of.”
Interested in Advertising with CALSAFE
The California Association of Life Safety and Fire Equipment (CALSAFE) is pleased to announce our new advertising program for 2016. Your organization will be able to efficiently maximize your marketing dollars through CALSAFE’s uniquely targeted advertising program that offers exposure through our quarterly newsletters, our website and at our Annual Meeting.
Ask the Expert
Co2 Fire Extinguishers
When are Co2 fire extinguishers obsolete?
I know about the regulations for stored pressure dry chemical and water, but I'm not sure where to find out about Co2. Is it something to do with the classification of B1 C1? Are there any restrictions on the age of the cylinder like in dry chemical stored pressure extinguishers? Any info. or D.O.T. links you can provide would be helpful.
1) Under obsolete extinguishers in Title 19 577.2
(11) states that any stored pressure fire extinguisher manufactured prior to 1955.
So any CO2 older than 1955 is obsolete.
(12) states that any extinguisher that has a 4B 6B 8B 12B and 16B fire rating.
Part of the justification for this item stated that these are old ratings do not meet the current rating requirements for the selection and placement of fire extinguishers in Title 19. They achieved their rating using different test scenarios than adopted today, and there are no parts left available for these extinguishers rending them unserviceable.
While we do not have the date the rating system changed, any CO2 extinguisher that has these “obsolete” rating numbers is obsolete and is to be replace.